The fireguard FG roller shutters are a range of fire protection barriers that automatically operate in an emergency situation once a signal is received from a fire alarm system.
The Fireguard FG Range is a fire roller shutter that can be specified as:
Constructed to the latest safety standards BS EN 1634-1 & BS 476 Part 22 this electric roller shutter is manufactured from 76mm cold rolled 20 gauge galvanised steel sections.
The fireguard FG shutters are safety device’s that form a protection barrier against the spread of property fire for up to 4 hours and can be linked to many closing requirements such as audio alarm, visual beacon, time delay or subject to local fire officers advice.
Tested Report Number WF314225 - BS 476 Part 22 & BS EN 1634-1
The Fireguard FG Range roller shutter is best used in kitchen survery areas, warehouses, commercial areas where fire segregation is needed yet walk through or general day to day access is required.
Normally 76mm x 0.71mm
11.32kg per square metre (dependant on size)
Galvanised bright rolled mild steel but polyester powder coat colour's are available at additional cost.
1.5mm bright spangle galvanised pressed steel coil casing available in various different designs to suit individual circumstances.
Overall height (top of box)
Up to 3500mm box size 350mm
Up to 4250mm box size 375mm
Up to 5250mm box size 400mm
Up to 6000mm box size 450mm
Up to 8000mm box Size 600mm
On larger widths the box sizes may move up one size due to deflection.
Galvanised steel standard, polyester powder coat colours are available.
Barrel Support Brackets must be installed subject to size and fire integrity required.
63mm x 32mm x 3mm - 100mm x 32mm x 3mm Dependant on Width and Height.
Galvanised steel standard polyester powder coat colours are available
Electrically operated through industrial grade 1 phase motor controlled by up/stop/close controller.
Auto Reset solenoid for integration with fire alarm to enable the motor to automatically unbrake and close under controlled decent.
FCP03 Fire panel which can be interconnected to the Fire Alarm to allow closing when receiving fire signal. Audio visual warning and timer delay.
Further safety devices are available, dependant on requirements and operational circumstances.
Important note: Maintenance of fire shutters is required under the Regulatory Reform (Fire Safety) Order 2005 for companies. Failure to do so may invalidate insurance cover and building fire certification under the control of the local fire officer.
It is essential that the structural surround to the opening has a fire rating o at least the equivalent to the fireguard product specified and is sufficient for fixings to ensure fully compliant installation.
Product specification may change and it is advisable to consult with HAG technical advisors before specifying or ordering. HAG operates a policy of continuous improvement.
Product specification may change and it is advisable to consult with HAG technical advisors before specifying or ordering.
HAG operates a policy of continuous improvement.